In power engineering, the power-flow study, or load-flow study, is a numerical analysis of the flow of electric power in an interconnected system. A power-flow study usually uses simplified notations such as a one-line diagram and per-unit system, and focuses on various aspects of AC power parameters, such as voltages, voltage angles, real power and reactive power. It analyzes the power systems in normal steady-state operation.
Power-flow or load-flow studies are important for planning future expansion of power systems as well as in determining the best operation of existing systems. The principal information obtained from the power-flow study is the magnitude and phase angle of the voltage at each bus, and the real and reactive power flowing in each line.
Commercial power systems are usually too complex to allow for hand solution of the power flow. Special purpose network analyzers were built between 1929 and the early 1960s to provide laboratory-scale physical models of power systems. Large-scale digital computers replaced the analog methods with numerical solutions.
In addition to a power-flow study, computer programs perform related calculations such as short-circuit fault analysis, stability studies (transient and steady-state), unit commitment and economic dispatch. In particular, some programs use linear programming to find the optimal power flow, the conditions which give the lowest cost per kilowatt hour delivered.
A load flow study is especially valuable for a system with multiple load centers, such as a refinery complex. The power flow study is an analysis of the system’s capability to adequately supply the connected load. The total system losses, as well as individual line losses, also are tabulated. Transformer tap positions are selected to ensure the correct voltage at critical locations such as motor control centers. Performing a load flow study on an existing system provides insight and recommendations as to the system operation and optimization of control settings to obtain maximum capacity while minimizing the operating costs. The results of such an analysis are in terms of active power, reactive power, voltage magnitude and phase angle. Furthermore, power-flow computations are crucial for optimal operations of groups of generating units.
In term of its approach to uncertainties, load flow study can be divided to deterministic load flow and uncertainty-concerned load flow. Deterministic load flow study does not take into account the uncertainties arising from both power generations and load behaviors. To take the uncertainties into consideration, there are several approaches that has been used such as probabilistic, possibilistic, information gap decision theory, robust optimization, and interval analysis.
An alternating current power-flow model is a model used in electrical engineering to analyze power grids. It provides a nonlinear system of equations which describes the energy flow through each transmission line. The problem is non-linear because the power flow into load impedances is a function of the square of the applied voltages. Due to nonlinearity, in many cases the analysis of large network via AC power-flow model is not feasible, and a linear (but less accurate) DC power-flow model is used instead.
Usually analysis of a three-phase power system is simplified by assuming balanced loading of all three phases. Sinusoidal steady-state operation is assumed, with no transient changes in power flow or voltage due to load or generation changes, meaning all current and voltage waveforms are sinusoidal with no DC offset and have the same constant frequency. The previous assumption is the same as assuming the power system is linear time-invariant (even though the system of equations is nonlinear), driven by sinusoidal sources of same frequency, and operating in steady-state, which allows to use phasor analysis, another simplification. A further simplification is to use the per-unit system to represent all voltages, power flows, and impedances, scaling the actual target system values to some convenient base. A system one-line diagram is the basis to build a mathematical model of the generators, loads, buses, and transmission lines of the system, and their electrical impedances and ratings.
The goal of a power-flow study is to obtain complete voltages angle and magnitude information for each bus in a power system for specified load and generator real power and voltage conditions. Once this information is known, real and reactive power flow on each branch as well as generator reactive power output can be analytically determined. Due to the nonlinear nature of this problem, numerical methods are employed to obtain a solution that is within an acceptable tolerance.
The solution to the power-flow problem begins with identifying the known and unknown variables in the system. The known and unknown variables are dependent on the type of bus. A bus without any generators connected to it is called a Load Bus. With one exception, a bus with at least one generator connected to it is called a Generator Bus. The exception is one arbitrarily-selected bus that has a generator. This bus is referred to as the slack bus.
In the power-flow problem, it is assumed that the real power PD and reactive power QD at each Load Bus are known. For this reason, Load Buses are also known as PQ Buses. For Generator Buses, it is assumed that the real power generated PG and the voltage magnitude |V| is known. For the Slack Bus, it is assumed that the voltage magnitude |V| and voltage phase Θ are known. Therefore, for each Load Bus, both the voltage magnitude and angle are unknown and must be solved for; for each Generator Bus, the voltage angle must be solved for; there are no variables that must be solved for the Slack Bus. In a system with N buses and R generators, there are then unknowns.
In order to solve for the unknowns, there must be equations that do not introduce any new unknown variables. The possible equations to use are power balance equations, which can be written for real and reactive power for each bus. The real power balance equation is:
where is the net active power injected at bus i, is the real part of the element in the bus admittance matrix YBUS corresponding to the row and column, is the imaginary part of the element in the YBUS corresponding to the row and column and is the difference in voltage angle between the and buses (). The reactive power balance equation is:
where is the net reactive power injected at bus i.
Equations included are the real and reactive power balance equations for each Load Bus and the real power balance equation for each Generator Bus. Only the real power balance equation is written for a Generator Bus because the net reactive power injected is assumed to be unknown and therefore including the reactive power balance equation would result in an additional unknown variable. For similar reasons, there are no equations written for the Slack Bus.
In many transmission systems, the impedance of the power network lines is primarily inductive, i.e. the phase angles of the power lines impedance are usually relatively large and very close to 90 degrees. There is thus a strong coupling between real power and voltage angle, and between reactive power and voltage magnitude, while the coupling between real power and voltage magnitude, as well as reactive power and voltage angle, is weak. As a result, real power is usually transmitted from the bus with higher voltage angle to the bus with lower voltage angle, and reactive power is usually transmitted from the bus with higher voltage magnitude to the bus with lower voltage magnitude. However, this approximation does not hold when the phase angle of the power line impedance is relatively small.
There are several different methods of solving the resulting nonlinear system of equations. The most popular is known as the Newton–Raphson method. This method begins with initial guesses of all unknown variables (voltage magnitude and angles at Load Buses and voltage angles at Generator Buses). Next, a Taylor Series is written, with the higher order terms ignored, for each of the power balance equations included in the system of equations . The result is a linear system of equations that can be expressed as:
where and are called the mismatch equations:
and is a matrix of partial derivatives known as a Jacobian: .
The linearized system of equations is solved to determine the next guess (m + 1) of voltage magnitude and angles based on:
The process continues until a stopping condition is met. A common stopping condition is to terminate if the norm of the mismatch equations is below a specified tolerance.
A rough outline of solution of the power-flow problem is:
Direct current load flow gives estimations of lines power flows on AC power systems. Direct current load flow looks only at active power flows and neglects reactive power flows. This method is non-iterative and absolutely convergent but less accurate than AC Load Flow solutions. Direct current load flow is used wherever repetitive and fast load flow estimations are required.